Protecting IT Equipment ProtectIT
ProtectIT: Protecting IT Equipment from Construction Dust: IT Equipment Protection
One of the biggest sources of particulate (dust) contamination of IT equipment is dust created during refurbishment work. The dust created is very small and very abrasive and therefore very damaging to moving parts of the server i.e. fans etc. The most damaging construction dust will be from one of two sources: silica based dust, from concrete, mortor, sandstone ect and low toxicity dust like plaster and plasterboard. Construction dust is produced in vast quantities and is very small (0.3μm (0.0003 of a mm) micron and up). This dust will quickly block airways causing overheating. Contractors often fail to effectively protect your mission critical equipment. This is due to the contractors lack of appreciation of how small these sub-micron particles are, and how they behave. Also dust like plaster dust has deliquescent relative humidity (Critical Relative Humidity) lower than the data centres relative humidity so will absorb moisture from the air and become damp, this will promote corrosion (sulphur & copper creep etc} and/or ionic migration (polarity changes) which will damage your equipment. Put in simple terms Plaster dust will absorb moisture from the air, become damp (eventually dissolving in the liquid) and damage the electronics in the equipmet. If you ever walk in a room with plaster dust present you will notice your mouth dry's quickly this is the plaster dust absorbing the moisture in your mouth.
IT Cleaning Ltd can use its IT Equipment Protection system to enclose the IT Equipment or the work area. Then using HEPA filtered air scrubbers, we will create a positive or negative pressure, which will ensure dust from the work area, can not migrate into the IT Equipment. By either keeping it out (enclosing IT equipment, positive pressure) or keeping it in the work area (enclosing Work area, negative pressure). We can control and monitor temperature within the enclosure to ensure equipment can continue to work whilst the refurbishment is happening. We will take air particulate readings of both work and clean area to prove the system is working.
"We have used this our IT Equipment Protection system in Data Rooms, Comms Rooms and even Broadcasting Apps Rooms. To date, it has worked every time. No contamination of the protected IT equipment has occurred." Stephen Yates MD.
While Protecting IT Equipment we can supply a manager to manage control of the contamination. Such as egress into and out of the space,....using air lock doors. Provide HEPA filtered vacuums for use by the contractors. Monitoring Particulate levels within the protected space. Maintaining pressures, air scrubbers and temperature.
After the construction work is finished we will technically clean any areas that require cleaning. Provide air particulate reading to prove the room and work areas are safe, then remove the enclosure. Handing the whole room back to the IT or Data Centre Manager. We will use the air particulate level class 8 from ISO 14644 which allows 3,520,000 particles at 0.5μm, 832,000 at 1μm and 29,300 at 5μm. For information on particle sizes click here What Makes up Sub Micron Particles
We are able to enclose the work/clean area. Using HEPA filtered air scrubbers we will create a negative/positive pressure within the areas. This will ensure the dust is unable to migrate from or into the enclosure depending on which way around we are doing the system. What particles do HEPA filters filter.
0.3µm Air Scrubbers will filter 2500m3 of air per hour. They are used to clean particulate which is forced airborne during cleaning so it can not resettle. We also use them to create a positive or negative pressure in an enclosure so the dust can not escape into the environment.